Best practice on specifying, designing, commissioning and operating control rooms
STANDARDS and guidance relating to control rooms have been available for many years but the reality is that it is widely accepted that control room design is often poor. Often the design is left to engineers who either do not recognise the importance of human factors, or perceive the available guidance to be inappropriate for ‘real life’ application.
If you have been tasked with designing a new control room or making significant modifications to an existing one, where would you even start? So many questions – from colour schemes to fish tanks to display and monitor settings and more besides.
If this is you, then worry not, help is at hand, in the form of a new edition of EEMUA 201 (3rd Edition, Control Rooms: A Guide to their Specification, Design, Commission and Operation), which was published earlier this year.
Rather than a simple update, the opportunity has been taken to develop a complete guide to designing and evaluating all aspects of new and existing control rooms and associated human machine interfaces (HMIs).
In an ideal world every control room design team would have access to competent human factors support. In the real world this is not always practical or possible. The guide aims to direct designers to recognise the human factors and actively involve control room operators (CROs) in the process.
EEMUA 201 covers a very important subject. The role of the CRO in managing risks of modern process plant is indisputable. Detecting deviations early, diagnosing the causes reliably and responding promptly and appropriately all contribute to the avoidance of major accidents and reduce reliance on automated systems. To do this, CROs need to be healthy and alert, all of the time. The design of the control room and HMI are significant human performance influencing factors.
A key aim with this update has been to put a stronger focus on human factors throughout. Design is a compromise. There is no single correct solution and often theory does not match practical experience. The guide highlights the decisions that need to be made, and gives information that can be used to achieve an optimum solution. The guide has been updated with input from a wide range of people with an interest in control room design, with a significant input from current CROs who are particularly important as they have to use whatever the designers come up with.
The updated guide sets out to answer a number of questions that are often asked about control room design, where the clear and practical answers have not always been easy to find. For example:
One of the challenges when updating a guide on control room design is that technology is changing so rapidly. This presents great opportunities but also risks. The guide includes some high-level information about some of these emerging issues to raise awareness and to prompt people to check the latest good practices. For example, technology that allows access to control system data and controls from outside of the control room is already available and becoming more prevalent. People accessing data from their desktop computer, tablet or mobile phone can enhance teamwork and data analysis but can cause confusion about who is in control and who responds if things go wrong. Also, it is one of many potential security issues. Security threats are continually evolving and new solutions are being developed in an attempt to catch up. The guide highlights that issues such as remote access and security need to be recognised very early so that developing solutions is an integral part of the design, and not handled as an add on at a later date. A security risk assessment should be a key activity to determine the level of threat and vulnerability of the systems being used.
EEMUA 201 is not a standard and is not intended to replace any. Its role is to provide guidance on how compliance can be achieved as part of a wider context of striving to provide the best control room possible to the CRO end users.
The guide aims to provide practical support to anyone with responsibility for control room design. If you are designing a new control room or making significant modifications to an existing one the guide includes a template for a human factors integration plan (HFIP).
This is a powerful tool for identifying the potential human factors issues and opportunities at an early stage in the project and for managing implementation of appropriate solutions to achieve an optimal design. The template includes a mixture of standard text for you to adapt to your project and prompts for when you need to delve deeper or obtain specialist support. A key message is that you want to start generating a HFIP as soon as possible in a project, and plan to review it and keep up to date throughout.
If you have been given the job of reviewing a control room design, whether this is for a new project or an existing control room, the guide provides a comprehensive checklist that will guide you through all the important issues to consider, and directs you to the sections in the guide which will help you make your evaluation.
It is not simply a tick-box exercise because every control room is unique. Instead it assists you in deciding if design is optimised and to determine if the inherent risks are being managed effectively. Clearly there are far more existing control rooms than there will be new projects at any time.
Using the checklist provides you with a basis for a gap analysis that you can use to decide if risks are as low as reasonably practicable (ALARP) and to prioritise any actions for improvement.
Catch up on the latest news, views and jobs from The Chemical Engineer. Below are the four latest issues. View a wider selection of the archive from within the Magazine section of this site.